However, if the boiler is installed in a compartmentor small room, some. ventilation air is necessary to maintain an acceptable temperature in the boiler area. 550mm²/kW 550mm²/kW 1100mm²/kW 1100mm²/kW of boiler output. Balanced flue boiler in room does not require individual ventilation.
Publications 'Guidance Notes For The Installation Of Domestic Gas Condensing Boilers' and 'Specification For Domestic Wet Central Heating Systems'. 1.4 PERFORMANCE DATA Celsius 25 Celsius 25P Nat. Gas (G20) LPG (G31) Max. Input (Gross CV) kW/(Btu/h) 26.1/(89,000) 25.0/(85,300) Max. Output To Water
The Secretary of State, in exercise of the powers conferred on him by sections 15(1), (2), (4)(a), (5), (6)(b) and 82(3)(a) of, and paragraphs 1(1), (2) and (3), 4(1), 12, 15(1) and 16 of Schedule 3 to, the Health and Safety at Work etc. Act 1974() (the 1974 Act) and of all other powers enabling him in that behalf and for the purpose of giving effect without modifications to proposals
User manual and Installation instructions - Biasi
British Gas - 330 - FREE BOILER MANUALS
Keep the boiler clear of dust during installation and in particular do not allow any dust or connection. Because every boiler is fired and tested live at the factory, a small amount of water re-mains within the boiler. It is possible for this water to initially cause the pump to seize. 4.5 Hydraulic specifications .. 30 4.6 Expansion
Connection of the whole electrical system of the boiler, including any heating controls, to the electrical supply must be through one common isolator and must be fused 3 Amp maximum. Isolation should be by a double pole switched fused spur box, with a minimum gap of 3mm for both poles.
Boiler Specification 2 Instructions for installation and servicing ecoMAX Boiler Specification 2 2.1 Technical data (1) ecoMAX ecoMAX ecoMAX Units 824/2 E 828/2 E 835 E Maximum CH heat input (G 20) (net) 18.4 22.4 27.0 kW Maximum CH heat input (G 31) (net) 18.4 22.4 27.0 kW CH heat output range
The boilers are easily mounted on any internal wall and can be installed with either a horizontal or vertical RSF (room sealed fan assisted) flue. The boilers use a standard flue system (100 mm or 125 mm outside diameter). Flue extensions and addition-al bends and elbows are